DC2 UNDER CONSTRUCTION
Pre-leasing opportunities available now
DC2 IN BARKER DIGITAL CAMPUS
DC2 is the second Next Generation data centre to be constructed in the five-building digital campus in Richmond Hill, Ontario.
Offering a highly-reliable 2N design – to ensure an uninterrupted power supply – and with a Power Usage Effectiveness (PUE) of 1.2 annualized or better, UDCS clients benefit from a significant power saving.
With white space available, DC2 will provide turnkey and colocation alternatives to clients looking to take advantage of one of the most robust fibre-optic networks in North America, highly reliable power and at-scale development with further room for expansion.
140 million residents within a 500km radius
One of the most robust fibre-optic networks in North America
There is almost 500,000 SF of data centre space on campus
Building size 94,691 SF Utility power PowerStream, 27,600 volts Parking 41 parking spaces Number of storeys 1 plus mezzanine Loading docks 2 indoor with dock levellers
COMPUTER ROOM SPECIFICATIONS
Available rooms Multiple Standard critical power 1.5 MW per data hall, upgradable to 2.0 MW High density ready Yes Approximate size 10,000 SF for IT equipment Maximum cabinet space Variable 550 standard 24’W x 48”D or 330 standard 32”W x 48”D
COMPUTER ROOM DENSITY
Standard density 150 watts per square foot Optional density 200 watts per square foot
COMPUTER ROOM DESCRIPTION
Computer rooms Dedicated Floor height Slab on grade, 18’ building height Floor to ceiling height Base design with drop ceiling 12’6” to 13’6” Floor loading 200 pounds per square foot
Building and perimeter Security check point for all access, ballistic glass and walls Security guards Yes, 7x24x365 Access control Yes, electronic access with dual authentication, minimum 1 biometric reader Video surveillance Yes, 7x24x365 of all exterior and interior areas, minimum 30 days of archive
Total megawatts 8 or 16 MW as required
Description High efficiency static UPS Redundancy N+1 or 2N as required
Description 2.5 MW diesel generator Redundancy N+1 or 2N as required
ON SITE FUEL CAPACITY
Storage tanks Sub-base tanks or underground as required Fuel runtime 24 hours minimum
HEAT REJECTION SYSTEMS
Description Distributed and Redundant KyotoCooling systems dedicated per data hall. Or Chilled Water solution to spec Redundancy N+1 Efficiency Mechanical PUE of 1.2 Annualized or better Efficiency at utilization Unaffected by critical load utilization
Description 250 amp overhead busway, optional multiple 400 KVA PDUs, 480V primary, 400/230V secondary available Redundancy 2N
POE 2 separate network points of entry with diverse underground duct banks to metropolitan network Conduits Dedicated diverse conduits and risers to each data floor Multiple carriers Yes, data centre is carrier neutral
Description Double interlocked pre-action dry type sprinkler system with VESDA throughout building
*Some specifications listed are optional.